FIRE SUPPRESSION SYSTEM ACCESSORIES(629)
An addressable loop-powered multi-sensor, with smoke, heat and CO sensing elements. The unit offers 24 different modes of operation*1 and seamlessly matches the other sensors in the ESP Range. The CO sensing element can be used to detect smoke as well as life-threatening CO levels (acting as a CO alarm). ACD-EN Features Low profile Heat, Optical and CO sensing elements CO Alarm (COHb) facility 10 year CO sensor life Programmable fire threshold level RI & LED controllable separately if required*1 2 colour LED (Polling: Green, Fire: RED) Multiple modes
FireVu is a complete solution which can be used in a wide array of challenging environments for a variety of applications, unlike some other detection methods: Aspirating smoke detectors and beam detectors can only be used indoors and struggle with large voluminous areas as they rely on smoke reaching the beam or pipes. Historically they have issues with dusty, dirty environments triggering false alarms or going into a trouble/fault state as filters become blocked, resulting in frequent extra maintenance Thermal imaging cameras are often prohibitively expensive and unless accompanied by an additional CCTV image provide little or no situational awareness, preventing the end user or system operator from being able to identify the true nature of the risk and adopt the most appropriate course of action. Triple IR detectors have a limited range, the greatest of which is listed at 65m. A complete lack of any visual ouput means that any alarm received cannot be verified, with end users or fire authorities unable to assess the situation prior to attendance. Field experience has shown that this technology is susceptible to false triggers as a result of direct sunlight, either if used externally or from nearby entrances when deployed internally. FireVu solves this situational awareness issue through full visual verification, courtesy of the real-time video stream: Draws attention to exactly what triggered the alarm and where in the field of view it is through the use of coloured boxes. Lets you immediately know the size and scale of the fire so appropriate action can be taken. From allowing someone to tackle it with a fire extinguisher to immediately evacuating the building. Provides footage of the incident which will allow for post-event analysis to help determine the cause of the fire. This means processes can be improved and the site made safer in order to ensure there’s no repeat incident.
The Taktis product range combines the very latest hardware and software to produce a control and indication system, which is powerful and sophisticated, yet simple to use and understand. Intuitive interface The large graphical touch screen provides a clear, uncluttered and intuitive interface so the end user requires minimal training. Initially configured as a fire detection and alarm system, the flexibility of the Taktis platform is such that it can be re-configured to realise many other control and indication applications, with direct integration into intelligent buildings. Slot variants Available in 4 slot and 8 slot variants, with each slot supporting a 2 loop detection card, the Taktis fire control panel ranges from 2 to 16 detection loops. The generous quantity of sounder circuits, relays and inputs provided as standard can be further increased by the addition of one or mode Taktis I/O plug in expansion cards. The Taktis Network Card allows networking of up to 128 panels and repeaters meaning that Taktis can provide reassurance to all building owners/ operators whether responsible for a small system or a large complex.Add to Compare
The Apollo XP95 Optical Smoke detector uses an internal pulsing infrared LED and a photo-diode at an obtuse angle. In clear air conditions the photo-diode in the XP95 detector receives no light from the LED and produces a corresponding analogue signal. The signal increases when smoke enters the chamber and light is scattered onto the photo-diode. The optical smoke detector has a clear indicator LED which emits red light when the detector is in alarm.
The Badger B15V-1 industrial fire extinguisher is extremely versatile and ready to tackle flammable liquid and electrical fire hazards. It is ideally suited for indoor applications where delicate equipment or processes require a clean extinguishing agent. It’s suitable for use on Class B and C fires. Its features include: Heavy-duty chrome plated brass valve Stainless steel handle, lever and hose band Aluminium internal siphon tube 6- year warranty 5-year periodic hydrostatic test interval UL Listed and USCG approved - Meets D.O.T. requirements Easy-to-read two-piece nameplate 15-pound capacity
Edwards Signaling E-HD fixed temperature heat detector is an intelligent analogue device that can be configured as either a 135F fixed temperature heat sensor, or a combination rate-of-rise with fixed temperature. The heat sensor monitors the temperature of the air and determines whether an alarm should be initiated. The E-HD heat detector is capable of performing comprehensive self-diagnostics and storing the data. Due to its advanced thermistor technology, the E-HD detector is ideal for sensing fast, flaming fires and for applications where smoke detection is inappropriate. It is particularly well-suited to areas such as laundries and industries where fluctuations in ambient temperature is expected.
The Chubb Novec 1230 fire protection fluid is stored as a liquid and discharged into the protected space as a gas. It puts fires out quickly by a combination of heat absorption and chemical interference with the flame by reaching extinguishing concentrations in ten seconds or less. It does not leave any residue behind, and there is no need for costly clean-up operations. Since the fluid is at room temperature it is unique amongst gaseous agents and it therefore offers compact storage. It is electrically non-conductive and offers a safety margin of up to 100%, which is higher than any other type of clean fire suppression agent. The Novec 1230 fluid has a zero Ozone depletion potential, a Global Warming Potential of just one and an atmospheric lifetime of only five days.
Delta Fire hydrant valves are suitable for both offshore and onshore application. They are manufactured to BS 5154 and BS 5041 part 1. The valves are manufactured in corrosion resistant materials with a LG2 gunmetal body and are available with both British Instantaneous female outlet to BS 336 and a wide range of International outlets. All Delta Fire hydrant valves are dual seat type. The primary valve seat is hard rubber with an additional secondary metal to metal seat.
Brandschutz SECRETLY C 10 complies with EN 1866-1: P3-03 / 99 standards. Its operating temperature is -30 ° to 60 ° C, while its operating pressure is at + 20° C: 58 bar. Its typical applications include: electronic systems, chemical industry, areas with special hygienic requirements, machinery and equipment and more. The C 10 fire extinguisher is built of tubular steel and comes with a floor stand and holder for fire-fighting equipment. It’s throwing range is approximately 3 m and the fire hose length is 6 m. The SECRETLY C 10 is easy to handle and operate with no extinguishing agent residues. It’s environmentally friendly and easy to maintain.
The ANSUL® PREFERRED Commercial Low Pressure CO2 Fire Suppression System is designed to meet the requirements of NFPA 12, Standard on Carbon Dioxide Extinguishing Systems and is also Factory Mutual (FM) approved. The system consists of a low pressure storage unit, master valves, selector valves, manual and automatic controls, distribution nozzles, alarms, indicators, and supervisory devices as required to maintain a supply of carbon dioxide in a stand-by discharge ready state, and to provide effective distribution of agent on demand.
Chubb F850346N heat detector provides accurate temperature measurement data to the fire control panel. This intelligent analogue addressable device is compatible with the Chubb Controlmaster range of fire control panels. It provides a common communications platform for future integrated systems. The Enhanced Digital Systems Protocol (EDSP) has many unique features, including a very high level of data security.
Badger B-30-A carbon dioxide cartridge-operated extinguisher is fitted with low maintenance swivel discharge nozzle to accommodate both left and right-handed operators. It is designed with increased extinguishing agent for higher fire ratings, longer range, extended discharge times and higher flow rates. The B-30-A is UL Listed and USCG approved.
Victaulic V2702 is a standard and quick response upright fire sprinkler. The fire sprinkler is designed to produce a hemispherical spray pattern for use in light hazard occupancies which require minimal water discharge, such as bathrooms, closets and other small area applications.
The Badger ADV-20 fire extinguisher is ideally suited for addressing a wide range of DOT, USCG and commerical application market needs. It has an ergonomically designed handle and lever for ease of use. The valve threads are indexed to accomodate and permit field replacement. Additionally, heavy square thread on valve is designed for added ease of installation.
GST I-9102(UL) is an intelligent photoelectric smoke detector that can form part of a fire alarm system via connection to a fire alarm control panel. The detector illuminates to indicate its fire alarm status and transmits a fire signal to the control panel. Using infrared scattering technology, the detector receives very weak infrared light under normal smokeless conditions. If smoke particles enter the chamber, the received light signal will increase by scattering. When smoke density reaches a pre-set level, the detector will sound its alarm. In order to reduce interference and power consumption, the emitting circuit works in pulse mode to prolong the life of IR LED. GST I-9102(UL) smoke detector features: Electronically addressed Built-in microprocessor can store 14 history records Drift compensation, to suit extensive changing environments Self-diagnostic Standard: UL 268
Browse FIRE SUPPRESSION SYSTEM ACCESSORIES
Fire Suppression System Accessories products updated recently
While whole room protection – sprinklers or gas systems – is a common choice, there is an argument for thinking smaller; taking fire detection and suppression down to the equipment, enclosures and even the components where a fire is most likely to start. Traditional Fire Suppression Methods A traditional water-based sprinkler system is the most common form of fire protection found in commercial and industrial buildings. They offer reasonable cost, large area protection for entire facilities, safeguarding the structure and personnel by limiting the spread and impact of a fire. Every square foot of the protected area is covered equally regardless of the contents of the space, whether it’s an empty floor or an object with an increased risk of fire. Sprinklers aren’t always the most appropriate choice. Not all fires are extinguished by water of course, and in some cases, water damage can be just as harmful or even more so than the fire. They are an impractical choice for instance for facilities housing anything electrical, such as data centres and server rooms. There is also the risk of accidental activation, with an estimated cost of up to $1,000 for every minute they are left running. Water damage can be just as harmful or even more so than any fire, so sprinklers may not be appropriate Targeted Supplementary Fire Suppression An alternative method to protect whole server rooms and data centres is gas fire suppression, which either suppresses the fire by displacing oxygen (inert) or by using a form of cooling mechanism (chemical/synthetic). These aren’t without risk; in the case of inert gas, oxygen is reduced to less than 15% to suffocate the fire, but must be kept above 12% to avoid endangering the lives of personnel. Similarly, clean agent gas can be toxic in high doses. There are smaller, focused systems that give the option of highly targeted supplementary fire suppression within fire risk areas. Installing a system directly into the areas most at risk, means that fires can be put out before they take hold and cause serious damage. Both sprinkler and gas systems can contain a fire, but micro-environment or closed space systems are completely automatic, detecting and suppressing the fire so rapidly that activating a sprinkler or gas total flooding system often isn’t necessary. The most popular enclosure fire suppression systems achieve this though the use of a flexible and durable polymer tubing that is routed easily through the tightest spaces. The tubing is extremely sensitive to heat and, because it can be placed so close to potential failure points, detects it and releases the fire suppression agent up to ten times faster than traditional systems. An airline was forced to cancel over 2,000 flights after a “small fire” in one of its data centers Cost-Effective Fire Protection Highly customizable, small enclosure fire suppression is specifically designed to protect business critical spaces and equipment. It is typically used inside machinery like CNC machines, mobile equipment like forklifts and inside server rooms and electrical cabinetry but is suitable for any hazard that’s considered to have an elevated fire risk. Some may question the need or cost-effectiveness of protecting micro-environments. However, examples abound of where fires that have started at component level have gone on to cause damage of the highest magnitude, and the cost of downtime can be crippling to many time-sensitive facilities and processes. An airline was forced to cancel over 2,000 flights in August 2016 when what was described as a “small fire” in one of its data centers ultimately led to a computer outage. The cost of that small fire, and the domino effect that quickly escalated from it, has since been announced as $150m. Admittedly that number is unusually high - the average cost of a data centre outage today is estimated at a more conservative $730,000 – but this is still an expense businesses can ill afford. Preventing Major Losses Staying with the transport industry, newer metros systems have redundant systems in place to prevent interruptions. However, older metro lines, such as the one in New York City, have experienced electrical fires that started small, but grew to such a magnitude that service was affected for months.Older metro lines, such as New York City's, have experience electrical fires that start small but grew exponentially A wind energy customer experienced a fire in a turbine converter cabinet. The loss of the cabinet was valued at over $200,000 and disabled the turbine for six weeks. Following investment in fire suppression systems inside the electrical cabinet, a subsequent fire was detected and suppressed before major damage could be caused. The cost on this occasion was therefore limited to a $25,000 component and downtime was less than two days.Equally - happily - there are also many instances where the installation of small enclosure fire suppression has prevented disaster. In the manufacturing world, CNC machines are valued at hundreds of thousands of dollars and need to be constantly operational to justify the investment. Oil coolant used in the machines can create a flash fire in an instant due to failed components or programming errors. The fact that many of these facilities are run ‘lights out’ with no personnel present further exacerbates the risk. If a fire is not dealt with immediately, the machine will be destroyed; sprinklers don’t react quickly enough for this scenario and would be ineffective. Ensuring Business Continuity One such flash fire occurred inside a protected CNC machine at a machine shop in Iowa. The polymer tubing ruptured within a fraction of a second, releasing the suppression agent and extinguishing the flames. The machine was undamaged and was operational again with a few hours. Contrast this to a previous fire at the same facility in an unprotected machine; it was out of operation for 4 days, costing the business thousands of dollars in downtime In short, fire protection is an essential element of our industrial and commercial environments to ensure both safety and business continuity. However, the nature of that protection is changing, as capacity increases to cost-effectively protect specific areas where fires are most likely to start. Risk mitigation analysis needs to look beyond what has been accepted in the past and find ways to further limit the impact of a small fire using this next level of protection. The benefits can really have a positive effect on the bottom line in the event of fire.
The era of “smart buildings” is here, bringing new opportunities for significant gains in efficiency, safety and environmental protection. In an interview, Rodger Reiswig, director of industry relations at Johnson Controls Global Fire Protection Products, offers his insights into the impact of smart buildings on fire detection and what it means for organisations planning new facilities. Q: How do you define smart buildings? The term “smart buildings” means different things to different people. For some, it’s all about the Green Initiative. Is the building able to sustain itself or reduce its carbon footprint? Can they reuse some of their water or generate electricity from onsite solar cells or wind turbines? Another definition of “smart buildings” is based on sensors. Is the building smart enough to know that, if I’m the first person there in the morning and I swipe my card, it should switch the HVAC system into occupied mode? Can it start to turn the lights on? Can it adjust the window shades to allow the sun to come in? Can it call the elevator down for me because it knows that I’m in the lobby and I’m going to the tenth floor? It’s all about how the systems integrate with one another, not just providing information to each other, but also interacting with one another, causing things to happen from one system to another. Q: How close are we to the vision of an integrated intelligent building where all the systems work together? We’ve already been doing some integration for a few years now with things like HVAC and lighting. Now we’re seeing tighter integration where, for example, we can use the position of the sun to get the best impact of sunlight to start to heat the building in the winter. One of the biggest challenges that we see in the smart building environment is protocols or topologies for how one system talks to another. The fire alarm system uses a certain protocol or language. The HVAC system uses another protocol or language, and so on. Creating an environment where systems can talk to one another and not just send, but also receive information – that’s the difficult part. Everybody can send information out. It’s easy for me to tell you what is happening in a system. But for you to tell me what’s happening in your system and then expect me to do something with that information, that’s when it gets a little bit harder. Q: What makes system-to-system communication challenging? Because of the critical role they play in protecting lives and property, life safety systems require a level of reliability and resilience far beyond that of other building systems or networks. Therefore, we have to be extremely careful about how we allow information from other systems to come into the life safety system, in case that information should affect the performance of the system. In addition, the design and specification of life safety systems is guided via three different means: building codes, standards and listings. Each of those means is controlled by different organisations. Any proposed changes to life safety networks have to pass muster with those entities, and that takes time, effort and consensus-building. When we’re talking specifically about system-to-system communication, the listing entities, organisations like UL and FM Global, regulate how much information can come into any life safety system. The listing documents require that there be some type of a barrier or gateway to prevent unauthorised or corrupted information from coming into a fire alarm system, causing harm or causing it to lock up. Life safety systems require a level of reliability and resilience far beyond that of other building systems or networks We will see all building technologies become more integrated over time as we work through the different entities and people begin to realise the benefits of improved safety, lower environmental impact, and reduced costs. Q: How will fire detection systems benefit from other sensor information available in a building? One of the things being explored is occupancy sensors that tell where people are located in a building. Some type of telemetry could be used to understand where people are concentrated in a facility and, based on that, make the fire alarm system more or less sensitive to smoke. If a lot of people are congregating in one area, there might be more activity and more dust being stirred up. You could use that information to set different alarm parameters compared to, for example, an empty building with no significant air movement. We see that type of operation happening. Knowing how many people are in a building and where they are located is also a critically valuable piece of information for first responders. Here’s another example: let’s say we have a big parking garage next to a mall. Cars come in, and perhaps some people leave their cars running, or the cars aren’t operating as efficiently as they should be. You could have carbon monoxide detectors and occupancy sensors in the garage, and when the garage becomes crowded and carbon monoxide levels start to rise a bit, you could tell the fire alarm system not to go into alarm, but instead to turn fans on to get some fresh air moving throughout the building. It’s performing a life safety function, but at a non-emergency level. Q: Are you involved in any cross-industry standard-setting organisations to enable better communication among building systems? On an industry level, Johnson Controls is very active in the development of codes and standards. We have people who sit on committees for things like healthcare occupancy standards. We have engineers that contribute to product listing documents. We have people who participate in committees that determine how products should be installed and maintained.Fire alarm systems could be used to detect and solve non-emergencies before they become threats We’re even involved with groups, like the National Disabilities Rights Network, that advocate for laws that promote equal access and notification of life safety events. The list goes on. It’s a common protocol that allows all types of systems to get on the same communication platform and be able to send and possibly receive information, depending on the product and the type of system it is.Just to give you an example, there’s a standard called BACnet, Building Automation Control Network, which was developed by the American Society of Heating, Refrigerating and Air-Conditioning Engineers. BACnet is based on entities, so within their system, they need to define what each entity is. What is a thermostat? What is a variable air box? What is a lighting controller? What is a fire alarm smoke detector? We work closely with this organisation to create entities that can reside on their infrastructure so that, for example, the lightning system recognises what a smoke detector is when they send that entity out to the network. It’s one of the most important methods we are using to communicate among dissimilar systems. Integrated systems mean elevators could be used to evacuate people in an emergency We’re working on two fronts: internally and industry-wide. We’re developing third-party interfaces that enable an outside entity to sign a non-disclosure form and get the keys to the kingdom, if you will, on our protocols for how our systems operate – the data stream that we can send out and receive back – allowing that third-party developer to create some of these interfaces themselves. That has been one of our challenges, because we have always said that this is a fire alarm system, and if you want that type of an interface, we need to write it and get it listed. We had to step back and say, what if we developed a barrier gateway and allowed somebody else to develop the protocol and, done properly, became able to receive and send information to the fire alarm system? It’s like what Apple does with apps. We are going down that road with this third-party interface gateway. Q: Have these developments changed how you’re planning for the future development of fire detection systems? Yes, they have. We are looking at how we can use these systems strategically to make life safety systems better. And life safety is becoming more nuanced, proactive and comprehensive. Can I communicate and use this information to unlock the door so people have a clear egress? Can I start to use the elevators to evacuate people during an emergency? We’ve been told traditionally to use the stairwell and not the elevator in the event of a fire. But it takes a person about a minute a floor to get out. That’s a problem if you’re in an 80-story building. You have elevators sitting there. Is there something we could do to allow these elevators to be used to evacuate people? The American Society of Mechanical Engineers has been working hard on developing the language and requirements to do that. It’s just one example of how having systems integrated and talking to each other allows us to create smarter solutions that can help make facilities safer. Q: What advice would you give to building owners, architects, designers or contractors to help them start planning today for the future of smart buildings? The most important thing is to build awareness. The average building owner doesn’t know that a lot of this technology even exists. We need to inform them that there are options they can ask about. One of my recommendations would be to ask your design engineer. As you discuss the kind of windows you want, the kind of flooring and lighting and so on, ask how these systems could integrate together and what the benefits of integration would be. The bigger your facility, the greater the benefits of integrating these systems. Another resource that people don’t use often enough is the AHJs, the authorities having jurisdiction. That’s the local fire marshal, the fire chief, the local first responders. Don’t be afraid to sit down with a fire marshal, tell them what kind of building you’re putting in, and ask them what would help them respond in the event of an emergency in that building. They’ll be glad you asked, because these people see a lot of different buildings and respond to emergencies every day.
Interconnected smoke alarms provide an earlier warning and the best chance of escape In this article, Neil Perdell, National Technical Manager at Aico Ltd., suggests some crucial and simple steps to consider before deciding on a smoke alarm. Making a case for wireless smoke alarm systems, he also lists the key characteristics that one must consider when selecting such a system for installation. Wireless smoke alarm systems - key characteristics In today’s highly competitive electrical installation market, margins are constantly being squeezed, costs are rising, and every business needs a competitive edge. Installers of mains-powered smoke alarms, will no doubt know that they need to be interconnected within a domestic property to meet building regulations and standards. Interconnected smoke alarms provide an earlier warning and the best chance of escape. Traditionally these alarms have been hard wired together but more and more installers are now using wire-free/ wireless alarm interconnection, which uses Radio Frequency (RF) signals instead. They offer such time and cost saving advantages over hard-wired smoke alarm systems that, in these days of austerity, they’re a very sensible choice. But with more installers using them, alarm installers should pick a reliable system that is quick and simple to install in order to deliver a competitive advantage. Tips to find the right smoke alarm system - Listed below are some of the key characteristics and parameters that one must evaluate in a wireless interconnect smoke alarm system. Reliability The first real tip is to install the most reliable technology, something that really can be trusted to work. Call-backs are expensive. Struggles with poorly performing technology don't just waste time on site but can cause further problems later. Determining what is a reliable system from those available isn’t as easy as simply picking up a product and looking at it. One should check with colleagues to see what has worked for them and try to use a system that has been tried and tested over many years. Alarm installers should pick a reliable system that is quick and simple to install in order to deliver a competitive advantage A system that uses a multi-level repeater to pass RF signals from alarm to alarm is something else that should be considered. This ensures good RF signal strength in a property and provides multiple signal paths if an obstruction is placed in the way of a signal. While it may not seem an obvious issue, the question of back up in the event of a mains failure should be taken into consideration. If smoke alarms don’t work when they should, not only could there be liability issues, but this could result in fatalities as well. If possible, always choose a unit that has a 10-year rechargeable Lithium cell back up as standard as it is designed to outlive the life of the alarm itself. The battery backup should power both the alarm itself and the wireless technology so that the whole alarm system continues to work as normal and the system isn’t reduced to just standalone responses. Units that only offer conventional, primary battery backup should be avoided as these may need frequent changing and numerous surveys show that householders simply cannot be trusted to do this. Easy installation The next tip is to check just how simple the alarm system is to install and setup. Ideally, the terminal blocks should be built into the base and screw terminals to ensure reliable and robust connection. Check the units to see how much space is given to cabling. A useful feature to look for is the ability to make connections with the base off the ceiling or on. System setup should be examined well as this can catch people out, either because it is difficult and / or because it takes too long. A system that adopts ‘House Coding’ is a better option as this allows the individual alarms to be connected together very quickly. The best systems may have over 16 million codes – but others may have as few as 16. Generally speaking, the more codes the better – especially when installing systems in a number of properties close to each other. Here, having too few codes can mean serious problems, causing adjacent systems to activate each other. It is important to check the system setup to ensure that adjacent systems will not activate each other For simplicity, systems featuring dipswitches that need to be individually set to a certain combination on each unit in the system should be avoided. They tend to be small and difficult to use, making it far easier to make a mistake. Checking that the property has been successfully House Coded can also be quick – or complicated. Some systems have timesaving built-in indicators and a ‘House Code’ light on the base, which flashes to show how many units are connected to the system. For instance, if a property has five smoke alarms recently installed, the ‘House Code’ light will flash five times in sequence to show that all five have been successfully installed and interconnected. It’s an essential time saving feature. Form and function It’s also worth noting that some alarm systems offer greater functionality than others. This may enable installers to accept jobs that are out of the ordinary or more complex and demanding than usual. This might include the ability to ‘mix and match’; i.e. a system that allows extension of existing hard-wired systems to create a mixed hard-wired/wireless interconnected system (ideal for loft conversions). Accessorize! To get the most from a system, it is important to check what accessories are available. The best systems are available with alarm control switches, which allow for convenient Test, Silence and Locate functions – particularly important with larger installations. They enable the user to easily test every alarm on the system, identify which alarm has sounded and silence any nuisance alarms. This can all be done from one convenient, central point. It’s a great safety feature, as users don’t have to reach up to test a ceiling mounted alarm. The switch should also be wire-free and easily House Coded into the system. Other useful accessories to look for are relays, manual call points and switched input modules to provide application solutions. This flexibility can be enormous, as it allows the system to trigger flashing strobe warning lights or warden call systems for example. They can also interface with specialist alarm systems for the Hard of Hearing and – in some cases – with Carbon Monoxide alarms for a complete home safety system. While many wireless interconnect alarm systems may seem very similar at first glance, on closer inspection, their design and functionality can differ considerably. Choosing a quality, proven and reliable system is always the first and foremost consideration – because lives depend on it. Beyond that, choosing well-designed technology can make installation simpler, quicker and safer. Being familiar with additional functionality can add extra value to a job and enable installers to win more complex installations. Neil PerdellNational Technical ManagerAico Ltd.
Study By Persistence Market Research Reveals That Sales Of Fire Protection Systems To Surpass US$ 45.2 Bn In 2019
- Advanced’s Lux Intelligent system and MxPro fire panels protect The Berkeley in Knightsbridge
- Lussmanns sustains security and fire safety for staff and guests with Amthal Fire & Security
- Hochiki Provides High Performance Fire Alarm System To Yamaha Motorcycle Factory
- Logan County Emergency Operations Center implements MicroAutomation's NG9-1-1 software-based solution