BSI revises BS 7273-4:2015 code of practice for fire protection
BSI, the business standards company has revised BS 7273-4:2015 Code of Practice for the operation of fire protection measures - Part 4: Actuation of release mechanisms for doors. It was developed using collaborative input from the fire and safety industry with such organisations as The Fire Industry Association (FIA), Fire Protection Association and National Landlords Association offering guidance.
Fire doors are typically designed to be kept closed at all times so that fire and heat are contained and their spread minimised. This is achieved through use of well-engineered fire doors. However, on occasion they may be held open to facilitate convenience and/or accessibility around a building and in this situation mechanisms to hold them open, should follow BS 7273-4. This standard relates to the engineering of fire alarm systems and in particular mechanisms to interface with fire doors and secured fire exits. It addresses safety critical arrangements that enforcing authorities rely on to ensure a building can be evacuated safely - where fire doors are held open or exits secured which need to be released by the fire alarm system.
It is vital that there is a common approach to fire alarm design with regard to these interfaces. Especially as there is a responsibility for key stakeholders to meet relevant fire safety legislation. Previously, a device local to the doors effectively switched the doors to fail safe mode and released electrically secured fire exits and closed fire doors held open on magnetic door retainers. However, this is not always the case and a truly fail safe mode is not achieved. Therefore in some circumstances fire doors fail to satisfy enforcers that recommendations of BS 7273-4 are being met. As such BS 7273-4:2015 will help to clarify the expectations of users and match it to the technology available to the fire alarm industry.
Anthony Burd, Head of the Construction Sector at BSI said: “Until the development of BS 7273-4 in 2007, there was no code of practice with recommendations governing the interface of fire doors and the fire detection /fire alarm system, although there was guidance for the devices themselves. Imagine not having the security of knowing that a fire was contained because the doors had not gone into fail safe mode. Crucially, this revision gives fire safety enforcers the criteria for fail safe operation, and the standard goes even further by defining three different categories of actuation – ‘Critical, ‘Standard, and ‘Indirect’, each of which has a set of criteria for fail safe operation under defined conditions.”
Key changes to BS 7273-4:
BS 7273-4:2015 is of interest to fire alarm manufacturers and installers, enforcing authorities including building control bodies and fire and rescue authorities, fire consultants fire risk assessors.
Some of the others organisations involved in the development of BS 7273 include: British Cables Association, Chartered Institution of Building Services Engineers, Chief Fire Officers Association, Electrical Contractors’ Association, Fire Safety Association, Institute of Fire Prevention Officers, Loss Prevention Certification Board, National Inspection Council for Electrical Installation, National Security Inspectorate, Security Systems and Alarms Inspection Board and Royal Institution of Chartered Surveyors.
View all news from
Browse News by