Apollo updates and extends its XPander range of wireless fire detectors
Published on 22 September 2011
Apollo has updated and extended its XPander range of wireless fire detectors. Designed for use in areas where hard-wired fire detection is impossible or impractical, XPander devices are ideal for use in educational buildings such as schools and universities.
Educational establishments may typically consist of a number of buildings that are spread across a site, such as sports centres and exterior classrooms. Linking these buildings back to the main fire detection system can be expensive or impractical depending on distance and the large amount of cabling required. Apollo’s wireless XPander range solves this problem.
The extended XPander range includes two new products and now consists of an optical smoke detector, a multisensor smoke detector, heat detector types A1R and CS, a wireless base, a manual call point, a sounder and a sounder beacon and Single and Dual Input/Output Units. The complete range has been granted the new wireless link fire standard EN54 Part 25, which is the standard for European-compliant radio products.
XPander has an updated 31-device loop interface and connects to an XP95-compatible control panel via an interface which is wired to the loop. No special adjustment or programming is required and the devices are recognised by the control panel simply as another detector connected to the system. The detectors are multi-state in that they report normal, fire or fault states to the radio base, which transmits the information to the interface. The radio bases and signalling devices are addressable and use a pre-set analogue value to report via the XP95 protocol. In addition to ‘normal’ and ‘fire’ signals, the bases can also indicate a low battery, a dirty detector, detector tamper and low signal strength fault conditions.
View all news from
Browse News by